Amptec Electric Flow Boiler Installation Instructions and
SYSTEM 2000® FRONTIER - Energy Kinetics
(DHW by heat pump and boiler) (System diagram = 13, VR 70 configuration = 1) 11 System diagram 13 -5 12 13h eBUS bus coupler 48 Pressure gauge 14 Swimming pool controller 49 Flow meter (Taco setter) Legend for system diagrams -84 5 13 Item Description 63a VTK solar collector 64 Solar in-line vessel
§ Wiring diagram § Combustion Air Adapter § Temperature and pressure (T&P) gauge The customer should examine the equipment for any damage. It is the responsibility of the installer to ensure all parts supplied with the equipment are ! tted in a correct and safe manner.
The boiler can only be fitted in an engine room, adequate ventilation must be provided and this will be calculated at 5cm sq per kW of output. Note: - If the engine room is subject to a negative pressure air can be drawn into the compartment through the boiler flue system causing the boiler to be noisy and unreliable on start up.
12. Use either indirect/tank sensor or system/pipe sensor mounted on common return to the boiler. 13. Wire the tank or system/pipe sensor connected to the DHW sensor terminals on the follower boiler addressed as #1. 14. The system/pipe sensor must be placed on common piping to the tank, as close to the tank as possible. 15.
Commercial, Industrial, & Waste Oil Boilers 610-323-2700 Residential Sales 610-473-8457